1. MAIN USES:
The booster pump apply to transport liquid whose impurity content is lower than 1%
and the max particle size is smaller than 0.1mm, or whose chemical
and physical characteristics is similar to clean water.
They are always used on daily-use and fire-emergence water for tall
buildings. And they also can be used to supply water in mine,
cities towns, companies and low pressure boiler.
2. TYPE of Booster pump :
ISG: High pressure vertical pipeline booster pump, vertical inline
Up to 80Celsius Degree
ISG model booster pump is single-stage end-suction(axial suction) cantilever type
centrifugal pump, which is used to transport corrosive liquid with
viscosity similar to water and without solid particles. The marked
and rated performances and dimensions adopt international standard.
It has such characteristics as wide range of performance, high
efficiency, high mechanical, chemical and physical level and
convenient maintenance etc. It is energy saving type product
recommended by the nation with its efficiency being 5% greater than
that of other similar model pump.
The temperature of transported media of ISG model High pressure
vertical pipeline booster pump, vertical inline pump is -20 to 105 C deg . Through adopting
cooling method, it can transport media with higher temperature if
necessary, and is applied to transport various corrosive media or
media in which pollution is forbidden similar to water in such
industries as chemical industry, petroleum, metallurgy , electric
power, papermaking, food, pharmacy and synthetic fiber etc.
Tips for High pressure vertical pipeline booster pump, vertical inline pump installation
Please take note as below when install the pump:
1. The preformed hole on the foundation should be poured as the
pump installation drawing.
2. The installation level should meet the demand of the allowed
vacuum suction height. The foundation should be in horizontal and
stable condition, to make sure the rotation of the driver machinery
same with the pump in the direction.
3. When connect by coupling, must make sure the pump and driver
shaft center should be in a straight line.
4. If belt connection, the shaft center should be in parallel.
5. The booster pump suction pipe should be sealed well, and try to less the quantity
of the elbow and check valve. When fill water, exhausted the air.
It should be no any air when operate. We need to keep the suction
pipe slopes up slightly, and then connect with the pump inlet.